What people are saying - Write a review
We haven't found any reviews in the usual places.
Other editions - View all
accessible accordance with Section aggregate aisle applied approved area of refuge ASTM automatic sprinkler system B.W. gage braced wall lines building official building or structure ceiling cement combustible comply compressive strength concrete conform corridor Division 3 Occupancies doors dwelling units elevator equipment exceed EXCEPTION exit-access exterior walls fire assembly Fire Code fire-resistive construction fire-resistive rating floor area grade Group H grout gypsum hazardous height inches inspection installed insulation joists live load located masonry materials maximum means of egress minimum N/C less nails noncombustible occupancy separation occupant load one-hour fire-resistive openings panels percent perlite portion portland cement reinforcement requirements of Section roof rooms Select Structural sheathing slope smoke smoke detector space specified in Chapter specified in Section square feet stairways standpipes steel storage story studs surface Table thickness tion Type UBC Standard units vertical veneer ventilation vermiculite vertical in 12 water closet width wire wood